What are the Testing intervals?
Australian Standard AS/NZS 2293.2:1995 states that Exit and Emergency lighting must be tested in accordance to the procedures described in clauses 3.2.2 and 3.2.3, and not exceed intervals of no greater than specified, which is 6 monthly & 12 months. So in other words twice (2) a year
In accordance with Australian Standards 2293.2 emergency lighting systems are required to be tested & certified periodically, by conducting a 90 minute battery power down (discharge) test.
Testing & Tagging
Testing and Tagging your electrical appliances to make you compliant and your staff safe
RCD (Residual Currency Device), aka Safety Switch, perform a lifesaving job